Buy ASTM D R GUIDE FOR FLOOD TESTING HORIZONTAL WATERPROOFING INSTALLATIONS from SAI Global. note that ASTM D “Flood Testing Horizontal Waterproofing Installations” is the ASTM method from which this. Technical Data Sheet draws. ASTM D() – Standard Guide for Flood Testing Horizontal Waterproofing Installations0 item(s) – $ View Basket Welcom.
|Published (Last):||27 April 2012|
|PDF File Size:||10.69 Mb|
|ePub File Size:||7.76 Mb|
|Price:||Free* [*Free Regsitration Required]|
Note 2 — Increasing the amount of water forming a hydrostatic head beyond mm 4 in. This standard is not intended for use on building roofing systems. Adtm Enabling you to identify and mitigate the intrinsic risk in your operations, supply chains and business processes.
Flood testing is considered to be completed if no leaks are identified to have occurred during the test period and the membrane and flashings are intact. Water height is maintained so as not to exceed a minimum level of 2 inches below the edge of flashings. Through our network of over 43, people in 1, laboratories and offices in countries, Intertek provides quality and safety solutions to a wide range of industries around the world.
Referenced Documents purchase separately The documents listed below are referenced within the subject standard but are not provided as part of the standard. The values given in parentheses are for information only.
ASTM D – 98 Standard Guide for Flood Testing Horizontal Waterproofing Installations
Testing should occur prior to the installation of drainage layer, protection layer, pavers or overburden. Following the completion of the repairs and curing of materials, the area is retested under the same conditions as the initial flood test. The effects shall be analyzed by a licensed structural engineer prior to placement of additional loads. Evaluating how your products and services meet and exceed quality, safety, sustainability and performance standards.
Ponded water can freeze and become adhered to the waterproofing system resulting in pulling or tearing of the flashings away from the substrate or may break interior corners.
Assurance Testing Inspection Certification. Lateral loads will be imposed on curbs or walls used for containment of the water during the test procedures and their effect should be accounted for. See also ACI D Terminology Relating to Roofing and Waterproofing. A containment assembly is constructed to be nondestructive, non-penetrating of the waterproofing installation and easily removable. Applies for fully adhered or bonded sheet membranes, liquid or fluid applied ast or loose laid sheet membranes of waterproofing installed on parking garages and plaza deck types over habitable spaces or on elevated structures.
Testing is performed for a minimum of 24 hours and maximum of 72 hours when rainfall is not forecasted to occur. If a protection layer is required for flood tested, the recommended practice is that a temporary protection layer be loose laid and removed prior to testing of the waterproofing system.
The effects of equipment, planters, or other movable objects present within the test area should be considered. Waterproofing membrane and flashings should be inspected and deficiencies repaired.
Critical locations shall be monitored during the duration of the test period. Applicable waterproofing membrane installations that may be tested using this guide are fully adhered or bonded sheet membranes, liquid or fluid applied membranes, or loose laid sheet membranes.
Certification Formally confirming that your products and services meet all trusted external and internal standards. Validating the specifications, value and safety of your raw materials, products and assets. Work Item s – proposed revisions of this standard. Need help or have a question? Link to Active This link will always route to the current Active version of the standard. Containment assemblies are composed of a sacrificial sheet or a polyethylene sheet adhered to the surface of the waterproofing membrane using a watertight seal duct tape.
Global Reach Intertek is the industry leader with over 42, people in 1, locations in over countries. Overflows are provided in the containment assemblies, when needed, at 5 inches above low point on the test surface so as not to exceed the structural capacity of the substrate.
Auditing Consulting Sourcing Training.
Whether your business is local or global, we can ensure your products meet quality, health, environmental, safety, and social zstm standards for virtually any market around the world.
Historical Version s – view previous d597 of standard. Enabling you to identify and mitigate the intrinsic risk in your operations, supply chains and business processes. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
Testing Evaluating how your products and services meet and exceed quality, safety, sustainability and performance standards. Test area is flooded with water to achieve a ashm cover of 1 inch but not exceed a maximum depth of 4 inches d55957 the lowest point. Formally confirming that your products and services meet all trusted external and internal standards.
Inspection Validating the specifications, value and safety of your raw materials, products and assets. If leakage is detected during the test period, water is immediately drained from the test area. If the product does not meet the performance criteria, additional remediation may be required to pass.